To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Benefit of zoning with outdoor reset on MOD CON
1st post here.
I own an 2500sq ft poorly insulated 1850s greek revival in New Haven Ct. Last year we upgraded out boiler from an oil fired Weil McClain to a Burnham Alpine 150. Its set up with an indirect fire triangle tube DHWH on 1 zone and the rest of the house is heated on 1 MASSIVE zone. Thermostat is on 1st floor in the den on a wall that is in the middle of the house. Both zones are being run with grundfos 3 speed circulator pumps. I leave the thermostat @ 65F all the time. Really significant savings are already being realized, but the piping to each radiator was left as is to save on installation costs with plans to repipe in the near future.
What I want to do:
It looks like in the past the system was set up as a gravity piping system. The pipes get progressively larger "up to 4" CI pipes before they come back to the primary loop around my boiler. Luckily all the connections between pipes are in the basement. What I want to do is break the connections where multiple radiators are running off 1 pipe, build a manifold system and run home runs to each cast iron radiator from the basement. and create a seperate zone for the 1st and second floors. Bedrooms on 2nd floors, living space on 1st.
Will zoning the system will really save any money on my monthly gas bill when using the outdoor reset? I envision being able to set the 1st floor temp back a few degrees at night and 2nd floor back during the day. I've read that setting back the thermostat is counter productive with mod cons and ODR because it will cause the water temp to drop to the point where the boiler will have to refire back up to 100% when it could cruise @ around 20-40% like it does now when it gets to set point temp.
Any thoughts will help. I plan on repiping the basement for head room purposes with way, just wondering if it makes sense to go through the extra effort and cost of buying manifolds, an extra pump, relay, and tstat.
0 · ·