To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
New System but short Cycling
I just had a new Burnham IN5 unit stalled. I sized all my rads and the installer confirmed with his measurements. The new unit has one header up to riser split into 2 mains. Each main is insulated, still need to insulate the new riser/headers and loop.
Started the new gas boiler and the unit stops after 20 mins then started up again within 3 mins. the mains were hot but the rads were not. after the second cycle, the rads got hot and the termostats reached temp and shut the unit off.
Happened again the next day. I made adjustments to the temptrol with sub diff. to 1.5 psi main and 1 psi diff.
My question concerns the main vents. New vents were installed., each on the 2 mains. Vent-rite 33. They are convector vents rated to 6 psi. I calculated the 2 mains to .8 and .6 cf. Can't find out how to convert this to vent capacity. So is this ok? It hasn't been cold here in Massachusetts, but want to get the system ready.
I can post pics later when i get home. So any additional info can be get. Just wondering if my install went well. Thanks in advance.