To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Corroded flange on hot water output side of old crane 100w-150
The output side flange on the side of the boiler (residential) which connects to the hot water distribution circulation pump and plumbing has gradually been corroding over the years. It has a heavy buildup on the outside surface at this point - no obvious leak though. Would like to address before it fails outright.
I have been told it cannot be replaced on this old boiler and I thus need a new system. Which I don't want to do since, cost aside, you cannot buy a standing pilot resi boiler in this overly regulated state any longer.
As the boiler can still work with a standing pilot and gravity feed when the power is out I don't want to have to go to electronic ignition which won't work without power.
Can anyone confirm the flange cannot be replaced or repaired?
0 · ·