To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I think theres an issue with an install
I gave my niehbor some advise this spring when he got bids for a new gas boiler. 1: I asked him to have them install a drop header which he elected not to do and 2: run both dry returns down to meet the 28" drop then tie them together wet then into the boiler
The contractor instead left both dry returns tied together (as they already were) up high and tied them together about one foot above the boiler. I thought that this was the wrong way to do it. Will he have problems as a result of this? Is it acceptable to tie 2 dry returns together and only have about 1 foot of wet return.