To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Choosing a plan for my duplex
I recently purchased my first home, a purpose built up/down duplex I'm living in. It's a ~2500 square foot ~1920 structure in Upstate NY. It has completely separate utilities, and each apartment currently has very old gas boilers. My apt has a "newer" 1960ish cast iron gravity powered hot water boiler, and the other has the original coal burner with a gas kit and a pressure safety valve that looks like a physics class demo of a class 3 lever.
I'd like to replace these as a matter of updating infrastructure for reliability and efficiency, not to mention gaining some space and headroom in the basement.
My first floor apartment is ~900 square feet. Using loadcalc.net I come up with a design day heatloss of 24k BTU, and a design cooling load of 10k BTU. This squares well with my 5k window A/C that managed to keep the whole place quite comfortable all summer. The only assumption I'm very unsure of here is ceilings. Given that the ceiling is the uninsulated floor of another apartment presumably heated, I included zero heat loss through the ceiling. The installed boiler is 131k btu input. (huge?)
Using a couple different sets of tables, I've estimated the installed cast iron radiators at 25-28k BTU at the standard 180 degrees.
My goals are to upgrade to a modern system with that is considerably more efficient than the old, replace the failing DHW tank, while keeping the capital cost low. It'd be nice to add a warm floor to the bathroom, if I can do so without much expense.
My initial thought was something like this:
-AO Smith Vertex 76k BTU hot water heater with side loop
-Tempering valve for the DHW
-Taco XPB1 self contained heat exchanger/circulator/controller
-PEX manifold and home runs to radiators.
-If I'm feeling rich, a radiant loop in the bathroom?
Some concerns I have:
-Even though the place is OLD, and has all of the original radiators with none removed as far as I can tell, the heat loss seems similar to the radiation. And this is taking into account the insulation that has been retrofitted over the decades...foam under the vinyl siding and cellulose in the walls. Will I have enough heat on cold days with source water temps below 180?
-For efficiency, I'd want to operate the hot water tank at 140, not 170. I can't find any sort of automated reset control for the Vertex. Is there some other brand I should look at? Or is that just wasting effort and money for minimal gain?
-With efficient stuff installed and pex inside insulated joist bays instead of pipe knocking me in the head, how cold is this basement going to get?. The place came with the joist bays insulated...I've removed it all for now to solve a million unrelated old house problems, should I reinstall it or insulate the floors and walls of the basement?
Sorry for the wall of text, I just wanted to give all the background I could think of up front. Thank you for any advice you can provide.