To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I have a Triangle Tube Prestige 250 boiler hooked up to a Smart 40 Indirect Hot water heater. Which T&P relief valve am I supposed to use? The manual seems to have two suggestions - one based on tank size, the other on BTU - but they differ:
Determine T&P relief valve size by the follow- ing specifications, unless they conflict with local codes:
- TR 20/30/36/45 - SMART 20/30/40/50: 3/4”NPT with an AGA Rating of 100,000 BTU/hr. (Watts 100XL-8 or equivalent).
- TR 60/80/100/120 - SMART 60/80/100: 3/4”NPT with an AGA Rating of 200,000 BTU/hr. (Watts 40XL-8 or equivalent).
Also, the Watts 100XL-8 is about $14 from PEX supply while the Watts 40XL-8 is about $130.. Why is there such a difference in price? Something I'm missing?
THANK YOU IN ADVANCE!
0 · ·