To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Just looked at an old Smith 340 Mills boiler. The system has both radiator air vents and steam traps on other radiators. The boiler is set in a pit to maintain the "A" dimension.
The owner does not want to pay for the old boiler removal.
I'd like to install a new steam boiler higher then the old using a simplex condensate return pump and receiver.
? Do I need a steam trap before the receiver tank?
? Should the return piping remain at its current elevation? (in the pit)
0 · ·