To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Boiler exhaust & intake switched: how bad is it?
I'm a homeowner who is having trouble with my Peerless gas boiler (PI-80), in service without problems for about 5 years until a couple of months ago. I hired someone to take a look and the verdict is that I need a new combustion blower. After looking at the installation I see that the exhaust and intake are switched. The installation was supposed to use a T fitting (3" PVC) for the intake, extending about 6" from the outside of the house, and a straight PVC pipe extending at least 12" further out from the intake for the exhaust. Those two pipes are installed correctly but he hooked the straight pipe to the boiler intake and the pipe with the T to the boiler exhaust.
It doesn't seem like this should matter much to someone who otherwise has no clue, but how big of a screwup is this? How likely is it that this installation is contributing to exhaust gases getting into my intake? And if so, how likely would it contribute to my combustion blower breaking?