To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I was working on a carrier water source heat pump today (r410a) m#50 hq installed in april 2013.there was a certified air balance done on the unit, and airflow does not appear to be an issue.the problem is both circuits (6 ton two stage unit) are running with low suction pressure (95-100 psi) to the point where the outlet of the txv starts to ice up and the unit goes out on freeze protection. this occurs on both circuits. the charge has been removed and weighed back in to what is on the nameplate. even though this is a six ton unit with two isolated three ton circuits, the txvs are only rated at two tons each. does anyone else find this odd that you would have a six ton unit with txvs only capable of supplying four tons of refrigeration across the evaporator coil. both txvs seemed to be maintaining a good superheat (12-15 degrees) in the evaporator, it just seems that the evaporator is being starved of refrigerant, and the txvs cannot open any further
0 · ·