To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I’m a new homeowner with little experience with steam heat. I was hoping that some of the pros on this forum would be kind enough to help me with my question.
I’m renovating the whole top floor for myself. My contractor convinced me to exchange the bulky, column cast iron radiators with recessed Surad radiators – to save valuable space. In preparing the piping for the Sunrads, the plumber reduced the pipes to 1”. (note: he didn’t reduce any risers. each 1” pipe goes only to a single radiator). This got me a bit worried, since I noticed that the original pipes were wider.
He insists that 1” pipes are more than adequate for a single radiator. (on the top floor, there will be 6 Sunrads ranging between 12 and 14(16) sections, plus 2 smaller sunrads for the bathrooms).
My system is a 1 pipe steam system. It’s a 2 story building (plus an unfinished basement). The mains are 2” (from the boiler until the back of the house is aprox 25’, to front - 50’). The risers range between 1.25” to 2”.
Thank’s in advance for your guidance and advice