To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
What would cause a high subcool(35f)...and the Evap coil to freeze...this is a 5 ton split system r22 with txv....1 " 1/8 suction line.....5/8" iquid line.....line set over 120 feet.....condenser on roof air handler in basement....compressor amps below nameplate running at 12amps rated for 16 amps....another company was there two weeks ago....and I see a brand new head pressure control so the system had to be opened....non-condensables?...thank you Paul S
0 · ·