To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Water source heat pump loop and hot water system
Water Source heat pump system – I have used a boiler for direct heat add (boiler used only for heat add). I have used a boiler for an indirect heat add (heat exchanger). I don’t think I had a system the hot water system was directly coupled to the heat pump loop (hot water used for entry unit heaters and heating ventilation air). I can’t think of any reason I can’t have the loops directly coupled as long as I have a heat trap. Am I not thinking of something?
(I am talking about a regular water source heat pump loop - not a ground source).
0 · ·