To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I am adding in slab radiant to my current boiler radiant system. I have a few questions:
1)I understand i want to keep loops to 300'(1/2" pex O2 barrier)' or less at 250' what is a good pump size for 25X25X10 area well insulated? Spray foam insulated all around 6-8"thick.
2)I have a dunkirk QSM boiler w/outdoor reset heating via old cast iron(lower Delta T) It will be heating the house via this method. The Pex is for garage & basement slab and second floor of garage, I expect to need some mixing valves, can I use the return water loop as cold water supply to mixing valve? Should I "UPSIZE" the mixing valve?
3) I am planning on 3 loops(roughly 250' each loop) in the 25' X 25' slab spaced roughly 10" apart.does this seem reasonable? (Enough btu's to keep garage above 55 Deg F?) I know some of this answer is in question #1 flow rate and "head" of the pump
4) I am going to use "warmboard" insulated underneath for the floors that have an open area(heated) under them. Any comments?
5) I currently have a supply & return header supplying for 4 zones with an air scoop. do i need seperate air scoops for the pex zones?
Thanks,for your time and effort,Joe
0 · ·