To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Piping question for Quietside boiler / tankless install..
So I am installing a Quietside 120 in my own home. One of my two 40 gal went down and I just did not have the heart to simply plop another tank in there. I need space and want the high-efficiency as well.
My house is about 1700 sq', maybe 80k heatloss and I added some rads in the unfinished basement so including that maybe 100k. I have a front & back zone.
With 3/4" taps from the boiler, since I am zoning and may wish to add a zone some day, wouldn't a 2" manifold / buffer tube under the boiler with a primary pump be the best way to keep flow up? Then maybe 1" manifold off that for supply & return and mix in the buffer?
Working on steam and hot-water systems isn't rocket science....it's actually much harder.