To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
TT110 Trimax control question
In my effort to learn about my new TT 110 boiler, I have a question regarding the system pump operation selections in the trimax set up. You can select ch1/ch2/ dhw or just ch1/ch2 or only ch2. With my particular system I have circulators for all my zones including the indirect.
Should the system pump operate for every call in my set up? BTW, it is set on speed 1.
On a side note, I also have a system bypass left over form my old system, since I do not care about return temps, can I keep the valve closed now that I have the Triangle Tube?
Thanks in advance
0 · ·