To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I like the concept of a simple dual purpose boiler DHW producer. The Cadet uses a plate HX with a dedicated pump to provide instantanous DHW. The pump provides great flow and excellent DHW production, no pressure drop that you might expect with a 3 way diverting valve and a single pump.
Being empty nesters our DHW needs are low. With both the dishwasher and wash machine being equipped with timers we can space out the DHW loads, so only 1 draw at a time.
For a simple one temperature system, like mine this is an ideal boiler. A basic control does offer the ODR. It has a great sound deadening jacket.
The ThermoCon tanks buffers the 3 small loads, the low load being two small bathroom floors. The buffer is only warmed during the heating season, today and most of the summer solar or the DHW module provides DHW.
I do have a solar pre-heat tank so the Cadet DHW module does always see tempered water.
I'm also trying a SolarinCal valve from Caleffi. This assembly of 3 thermostatic valves selects between the boiler DHW or solar. If the solar tank is 110 or warmer the DHW module is bypassed. The valve also tempers the DHW should either the DHW module or solar tank exceed 113F.
0 · ·