To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
i recently installed a rheem tankless water heater(199,000 btu).....my boss told me to tap into the existing 1" gas line....now here is what is hooked up to this gas line....1" gas line 50 ft (= 245,000btuh) there are two warm air furnaces (1) 120k btu (1) 88,000 btu....and there is a dryer and stove on the line .....heating and water heater units are at the 50 ft mark....and the stove and dryer are about the 25' to 30' mark after the meter.....oh and gas meter is a 250cph.....i explained all this to my boss and he said he never had a problem with installing a tankless heater "as long as there is 3/4" line going to the unit"....i told him he would need a bigger gas meter and a 1" dedicated gas line to the tankless heater....he just brushed it off like they always do....my question is whenever i install a gas appliance on the side i always use a gas line sizing chart....when i install tankless heaters i run 1" gas lines from gas meters...hence i make less on the job...and i have lost some jobs due to charging extra for the dedicated gas line or upsizing meter/line....what is going on that these units are operating without any problems with undersized gas lines/meters....is it really that important....on paper to my customers it just looks like there paying more than they have too.....Paul S