To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I replaced a R22 condensor. Before evacuating with service valves closed, I pressure tested the lines and coil with 200 psi nitrogen. It dropped a little within 15 minutes. To make a long story short I couldn't isolate the leak, so I cut the lines at the evaporator, brazed a schraeder valve in and put 200 psi on the evap coil to see if it leaked. And while I was at it, I brazed the suction and liquid lines shut at the evaporator so now back at the condensor with the service valves still shut i could pressure test both lines individually with 200 psi. Here is the ball buster part, I went to lunch and came back, nothing dropped. WTF! Why would it drop when everything was connected, but not when eveything was tested individually? thanks in advance
0 · ·