To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
BoilerMate CH41Z aquastat differential?
Working at a customer's house today who complained of luke-warm water, but only part of the time. I confirmed the water temp to be 130 when I arrived, Amtrol BM installed Nov. 2012(not by me....finned tube HX big no no). Anyhow, I ran the hot water and confirmed the boiler's operation. Drained tank and filled with cold water, 32 minutes to heat 41 gal tank with Pensotti fired at .6 gph nozzle. Boiler did cycle a few times and is set to 160F. My question is, is there a way to tighten the differential on this type of "aquastat". It's mounted in a black plastic shroud with remote bulb. I pulled it out and didn't see any diff screw, but did notice there was a small screw in the shaft where the knob is attached like that in a gas range handle........ Any info much appreciated, this thing is still under warranty.
Always keep learning: observing what works, and what doesn't. Keep company who are smarter than you.