To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Alpine MCBA - indirect insltallation
NOT a PRO.
How can i get the Boiler loop circulator to run in either the heating system mode or DHW mode. The MCBA control has one wire for system circulator and another for DHW circulator.
When in DHW mode the DHW wire is energized and not the system circulator wire.
I guess this is for piping the indirect off the boiler loop when only 1 circulator for the indirect and boiler.
I'm connecting the indirect off the header pipe and I need the boiler loop circulator to run in both modes.
Can both these wires be connected to the boiler loop circulator so it runs in both modes.
I'm reluctant to do that because of the electronic control; i don't want to damage it.
0 · ·