To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Replacing boiler question?
I am about to have my CI boiler replaced with a new TT wall hung. I have a question about the size of the return piping. For my current boiler, the return piping is an inch and a 1/4 and for the TT 110, the return is 1 inch. My question is this, can I just keep the same near bolier piping 1 1/4 ( p & s) with 5 zones and reduce it to inch. I also am adding a 1 inch dirt separator to the new piping.
One of the zones is for my indirect. I know the TT has a separate DHW hook up. Do I just redo the piping to the indirect and eliminate that zone from the near boiler piping. The near boiler piping is all black iron. Thanks in advance
0 · ·