To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Hello, I am am looking for some help with a Taco HAFC 201 fan control. The control is interfacing with a hydronic air handler and the heating side is working correctly. Yesterday, I went to fire up a new 5 Ton condenser, (AC only) and wired up to the HAFC201 per the wiring diagram. The condensor starts and the fan starts with a slight delay. After about 2 minutes, both shut down, and the green led goes out but the red call for cooling remains lit. The control acts as if it is shorting out. It will reset after a short period, but repeats this condition. Has anyone had this experiance? Wondering if is an internal control problem or a wiring issue. Thanks in advance for some help with this.