To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Carlin 1150FD Flame Failures
Carlin 1150FFD with a Fireye control in a steam boiler. We did the maintenance, changed nozzles, electrodes, etc. Now we get random flame failures hours after running fine. The new nozzles were the factory recommended Semi Solid type. They gave us almost immediate flame failure. We put the old Solid nozzles back in, and now it will run for hours before failing. Seems to always fail overnight. It also won't run steadily unless the primary air is adjusted higher than normal.
I'm thinking a draft problem as the temperature drops at night...?
- Joe Starosielec
732-494-4357 ext. 2