To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Alpine MCBA - indirect insltallation
I'm a home owner considering installing indirect water heater, but I have a lot of ?'s.
1.my Alpine manual show the indirect piped off the boiler loop with it's own circulator.
but the new manuals show piping off the header near the loop.
Why the difference.
2.what's the pros and cons of these methods and piped as a zone with a zone valve.I already have a 1" zone valve on a zone i don't use.
3. The MCBA runs either the boiler circulator if switched with heating thermostat
connections, or the indirect circulator with the water heater connections.
Can I connect both of those circulator wires to the one boiler loop circulator
so that the boiler loop circulator runs under both situation?