To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Looking over existing steam system
Bought new house, looking over the existing one pipe steam system. Very satisfied owner of 'We've got steam heat!' and 'Greening Steam' . After reading both books I've noticed several things about my steam system that aren't quite up to spec.
It appears this "Steam Main" is a Vent:
My regular steam main is hooked up to cast iron, but the wet return is copper (which I think is OK):
However, it is flush to the floor, which might make it moderately difficult to insulate:
I've also noticed my supply lines are copper and not steel and as per my reading they can't flex with the pressure steam gives out. I can't seem to find the skim tap either:
Already cranked the pressuretrol down to .5 with a differential of one, I don't see the water surging that much. The boiler dates to 03/2000, Burnham Boiler Model: SIN4LNCP-LE2
Any other general best practices are welcome.
0 · ·