To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
HTP has two interesting products for combination heating and water heating. I wonder why they offer products which do the same thing differently. In other words, when would you use one versus the other
The Versa-Hydro heats 119 gallons of potable water. A Space Heating Module, consisting of a brazed plate heat exchanger and a variable speed circulator, attached to the tank. It pushes potable water through one side of the exchanger and the heating water moves through the other side.
The Versa-Flame comes in 50 gallon capacity. The 50 gallons is non-potable, operating at boiler pressure and used as the heating fluid. A circulator pushes boiler water through the brazed plate with potable on the other side for DHW.
The Versa-Hydro has a first hour rating of 335 gallons. After the tank is depleted, it will still recover 230 gallons per hour at a 70 degree F rise.
The Versa-Flame has a first hour rating of 300 gallons. Then it will do 288 gallons recovery at 77 degrees F rise. In other words, about the same, but a little better recovery.
So why offer both? Any ideas????
0 · ·