To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
finned tube convectors with modcon
I am looking at the energy use of a 7,500 sq ft administration building, and had a question for you folks. The building is heated at the perimeter with finned tube baseboard convectors (rough sketch of layout is attached), and they recently installed a new TT Prestige boiler.
The day I was there it was 40 degrees F outside and the boiler supply and return temperatures were 186 F and 182 F respectively (with 186 F target). There were high heat complaints throughout the building. I realize the new boiler is not set up correctly (not set up to run on the outdoor reset curve). My question is if the existing TRVs would be recommended once the boiler program is corrected, or is it better to remove them? The TRVs are located at the end of each FTR run. There is also a balancing valve at the end of each FTR run.
Any advice on best set up would be appreciated.
0 · ·