To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Indirect DHW tank Delta T?
In a primary/secondary boiler system a Taco 0010 is serving a Slant Fin WH-40 D indirect DHW tank. The Boiler is Trinity TFT 110(99,000 DOE). The manual for the WH-40 D says that is has 8 feet of head at 6 gpm and will give a 65 deg Delta T at 115 deg. Total head for the DHW loop is about 8.4 feet. At 8.4' of head the 0010 should move about 11 gpm. This is no doubt lowering the Delta T dramatically.
So here's the questions; what is the effect of a lower Delta T on the DHW Tank? How will if affect the 1st hour rating and how will it affect efficiency?
0 · ·