To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I have a 7 year old heating system. The boiler is Buderus oil G115 with logamatic and 60 gal tank. 5 zones of heating all valves the main pipe is 1 1/4" copper with 3/4" zone valves. The problem I am having is old ZVC506 yellow light are on dim when no t stat is calling and old valves are Taco ESP (black heads) are not closing all the way. So I change out the Taco ZVC506 box with new Taco ZVC506 and light are off like it should be. I got a call back 2 days latter and valves are doing the same thing not closing off all the way. I change all the Taco ESP heads out with new Taco Zone Sentry heads. I got anther call that same thing is happening to 1 zone not shutting off all the way. I change out the valve and head with Taco zone sentry. Same thing is still going on.
On the main there are 3/4" Ball valves before the zone valves. So I found out if I pull off head just past its lock down I can spin head around with a finger (360) no problem. As soon as I open ball valve with other zones on and house pump pumping (Taco 007) the valve locks up. I shut off ball valve and work it back and forth frees up and I can spin it around free again open valve it locks up.
0 · ·