To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
How do I hookup McDonnell & Miller Guard Dog RB-122 to Weil McLain CGI-5 Boiler
I have a Weil McLain CGI5 boiler. Previously I had a McDonnell & Miller Guard Dog RB-24 Low water cutoff (LWCO) hooked up to Weil McLain CGI-5 boiler. Since they are not sold anymore I bought a McDonnell & Miller Guard Dog RB-122. The wiring is a bit different. When I connect the 2 yellow controls from the RB-122 to the Yellow wiring (t-stat controls) on the WM control the T-stat is always on (calling for heat). I tried a different connection to the WM but ended up blowing the control module (fortunately it only cost me $70 from an Ebay seller to replace it instead of $150 & up from the local dealer). So to get my boiler to be controlled by my thermostats and not the RB-122 I have disconnected one of the RB-122 yellow cables. How should it be hooked up properly?