To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
WATERLOGGED 2 PIPE RETURN
WE SERVICE AN OLD COAL TO GAS CONVERSION (CONVERTED 1948?) TWO PIPE SYSTEM HANDLING A 3 STORY MUNICIPAL BUILDING WITH ATTACHED 1880s 3 STORY HOME. IN THE HOME WE HAVE A PROBLEM WITH A SERIES OF PARALLEL RADIATORS THAT BACK UP WITH WATER AND COOL OFF.
ALL HAVE 17C TRAPS ON THE RADIATOR DISCHARGE, AND F & T BUCKETS ON THE END OF THE SUPPLYS & ONE ON ONE RADIATOR RETURN
THE SET OF RADIATORS CAUSING PROBLEMS DRAINS INTO A 3/4 THEN 1, THE 1.5 THEN 2" IRON LINE, 7 FOOT OFF THE FLOOR. THE LINE SLOWLY DROPS THEN DIVES TO THE FLOOR RUNS FOR ABOUT 20' HORIZONTAL AND RISES INTO A MANIFOLD 2 FOOT OFF THE GROUND, AND INTO AN UNTRAPPED LINE ENTERING THE CONDENSATE PUMP.
IT APPEARS WE HAVE 2 OR 3 OF THE 7 RADIATORS WITH BAD T-STAT ELEMENTS (BAD IN THE CLOSED POSITION)
I AM THINKING THE MAIN PROBLEM IS A VACUUM BUILD-UP IN THE RETURN BECAUSE OF THE CLOSED / BROKEN T-STAT TRAPS NOT VENTING AIR / BREAKING A VACUUM, AND BACKING UP THIS ALREADY SERIOUSLY TRAPPED SYSTEM.
I AM CONSIDERING ADDING AN AIR VENT ( ANTLER SYSTEM) TO THE TOP OF THE BEGINING OF THE RETURN SYSTEM (GORTON #2s)
ANY OPINIONS OR ADVICE?
0 · ·