To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Backflow preventer question
I'm helping a neighbor skim his steam boiler (very dirty) and I am running into an issue that has confused me a bit. The installer put a backflow preventer in between manual feed valve and boiler. The valve has a copper pipe that comes out the side (vent?) and down into a big 5 gallon bucket. Everytime homeowner fills boiler via valve, a ton of water shoots out backflow valve and some into the boiler. This makes doing a slow skim challenging. Having never worked with a BFP, I dont know what's normal, but this just doesn't appear correct.
Can they be installed "reversed" and cause this to happen? Could there be crud in the valve? I started to feed the water and covered the end of the copper "downpipe" with my thumb. When I removed it, the flow had minimized and we are now able to keep a flow going into the boiler to do the skim.
Thanks in advance,
0 · ·