To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I received some great help previously getting started to understand my home's steam system ( http://www.heatinghelp.com/forum-thread/142756/Requesting-Help-to-Understand-and-Maintain-2-pipe-system ), and have a couple of questions about some next steps.
Summary: The system was installed when the house was built in 1937, and apparently is a vapor/vacuum system. Boiler is a Peerless JOT-5W installed in 1985.
Vaporstat - should I purchase a 0-1psi vaporstat or a 0-4psi model? Will I want/need to set the system pressure above 1psi? Or is it more important to have the finer adjustment capabilities of a 0-1 vaporstat instead?
Gauge - I will add a second, low-pressure gauge next to the vaporstat. Since the system develops vacuum during the heating cycle, do I need to find a 3-0-3 psi gauge, or will a standard 0-3psi gauge be ok?
Backflow preventer - there is a Watts 9D backflow preventer installed between the fill valve and the boiler ( http://media.wattswater.com/ES-9DM3_M2.pdf ) . I replaced it a couple of years ago thinking it was defective, but that didn't solve the "problem". After the thermostat is satisfied, there is a vacuum in the system, as confirmed by the 30-0-30psi gauge. Then I can hear air being sucked into the boiler through the vent/drain of the backflow preventer and water drips out the same opening. I can feel the vacuum and air movement by putting my thumb over the vent/drain opening. I'm not sure how much vacuum there should be in the system, but this "reverse venting" brings the vacuum down to zero. Is there a way to still have an inline backflow preventer but eliminate this problem?
0 · ·