To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
CSD-1 applicability question
I had understood that CSD-1 did not apply to boilers smaller than 400 MBTU/hr. As I start to read http://archive.org/download/gov.law.asme.csd-1.2009/asme.csd-1.2009.pdf I see CG-130 excluding really large boilers and swimming pool heaters, but CG-140 goes on to lay out a somewhat complex series of conditions for listed boilers under 400 MBTU/hr.
CG-140 (1) requires two things:
Compliance with all of part CW
Is this something we need to verify on a case by case basis?
Compliance with two specific paragraphs of CE-110
CE-110 (a) requires a lockable disconnect "at the boiler" and an external boiler room shutdown. The first aligns well with both NEC and mechanical codes. The second seems to imply that I need to include a solenoid-operated gas valve (as interlocked with kitchen hoods) on the plant main?
CE-110 (i) apparently forbids self-resetting controls after the primary?
0 · ·