To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
heat load calculation-HELP
Hello to all and thanks for any input, it is greatly appreciated. I am trying to keep this as short as I can, really. I have worked in the HVACR field for almost a decade and have recently started my own company. Now that I am on my own I am encountering certain situations that, although I am familiar with the concepts, I do not have a lot of practical experience with them. For example, heat loss/gain calculations. I went to trade school and have read manual J (I think its the abridged version). I constantly encounter houses where, for example, the top floors where the attic has been finished are too hot or cold.( I understand this could be a ductwork issue I have read manual D too). Many, but not all, of the contractors I speak to say that manual J (I wont say which one) is not accurate or that it undersizes or that it has just never worked for them. I had a situation with a room is a finished attic with one radiator. I calculated BTU of radiator (from lost art of steam heating) and heat loss of room and my calculation was that the radiator was more that sufficient. I dont want to simply oversize, I wantto be able to do a proper calculation, both for myself and for the customer. I am puting is a bid for a furnace replacement and the existing is 120,000 BTU, I would like to be able to know with confidence if it is oversized.
Any advice would be greatly appreciated
0 · ·