To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Can I get more efficiency from my old boiler?
Can I get more efficiency from my 1988 6 zone natural gas boiler? For example can an electronic igniter replace the pilot? Can a modulating burner replace the full on burner? Can it be adjusted and/or cleaned? I'm told there is nothing to adjust.
I live near Boston and keep the heat low but my gas CCF usage is 3-4 times my old similar sized house with condensing gas forced hot air furnace. New house has more window area and higher ceilings but better insulation and air sealing.
I started getting quotes on a Mod/Con boiler. But they run 4 times what it cost to install the condensing gas forced hot air furnace at the old house.
I mention the pilot/igniter because I can hear that it is a large flame. I turned off all thermostats and read the gas meter over an hour. The bottom dials on the gas meter are a bit hard to figure out but if I got it right the pilot is using 2 CF per hour, which is 14CCF per month or about 10% of November usage at the new house or 34% usage compared to old house. (These are rough numbers - I did not turn off HW)
Burnham P-208-W Installed 1988 Manufactured 1983
DOE HTG cap - 190,000
Water BTU/hr - 165,200
Input BTU/hr- 232,000
Gas pressure - 14 max and 4.5 min
Manifold pressure - 3.5
ASME max working pressure
Water - 30 psi
Min relief cap - 232
0 · ·