To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Peerless WBV-03 Beckett NX
Hello everyone. Im new to the fourm as a poster, but I read it often. My question is about my Peerless wbv-03. Its short cycling 3 mins max on a call for heat 5 mins or so for indirect call for heat. The unit has a beckett AFG with .75 80 b nozzle at 140 psi pump pressure. Quick online calculations state boiler is 3x to big for house (1100 sq ft). The beckett oem spec guide shows the nx burner with a .50 60 w nozzle (140 psi) the mbh output would then be closer to 2x oversized for house. My questions are with the new burner would the 65 mbh (ibr) output be large enough for my indirect (41 gal amtrol boilermate) and do you think i could significantly increase my run times on calls for heat, and finally would the increase in effieciency with increased runs times quickly pay for the (wholesale) cost of the burner. Thanks for any ideas
0 · ·