To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Close to perfect BUT...bangggg
Convert from oil to gas, of 100 yr old small colonial, 25' x 36', 7 current radiators (2 radiators removed decades ago) last month. Reputable local installed Burnham IN5 w/ electronic ignition, new auto feed, new Crown Megastor water heater (indirect). Issues with loud radiators, not enough pitch, and banging. Steam guru addressed with new vents, better pitch, alas quieter radiators - kids now aren't waking up at 4am. Yet, as the cycle near ends, radiators hot, vents doing their thing, there is a period of 3 minutes where extremely loud banging of pipes - from the second floor - seem to be heard coming from under the floor- not from radiators which are alongside the walls. The banging is extrremely loud. It's taken numerous readings (this is the great site!!) to address the various nuances to this new system. We are alomst there, as we enjoy a quiet home. This last burst of banging has us all up early and perplexed. What should I look for, to, and who is best to take a look at it?
0 · ·