To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I am replacing the entire burner unit in a Lennox O23Q2-70-1A oil furnace. The old unit used a R8184 M 1002 primary controller and the new one has a R7184B 1032. The old unit ran three wires to primary (24 volt power, WI, and Common) and the new unit only has two terminals( T and T). I have tried several combinations like 24 volt and WI to T and T and the burner would run but no blower until burner shut down. Also common and WI to T and T and that worked but no tstat control(stayed running). Tstat to primary and I don't get 24 volts to blower control. Is there a way to wire this and still have all safeties in place?
0 · ·