To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
I have a customer with a Bradford white direct vent water. It is serving a 35x35 garage with 5 lops of radiant 1/2 tube installed. It is unknown the legnth of the tubing. When we started the system the return water temp was around 50 degrees. It seems like it is taking forever to heat the slab. After 30 hrs the slab is now about 65 degrees. The input on the heater is 38,000 btu. The circulator return is pipd to the " hot" out on the water heater and the return piping is piped to the "cold" inlet. Not sure of the heat loss in the building.....