To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
hello to all. hope someone can point me in right direction. just bought an empty 2 family duplex foreclosure. it was an "as is" sale. no power or water on at time of close. house has 2 oil/hotwater boilers. both wm gold. both installed 2007. both have wm indirect hot water heaters. place was lived in till late july 2012. in apt "a", i got system bleed and running. aside from a slightly delayed ignition, which i tend to address with filter, screen , nozzle, adjust/clean probes and cad , check pressure,ect...... the problem is in apt "b"
wm gold boiler -2007
wm indirect water heater 2007
2 zones-1st floor/ 2nd floor
taco zone valves-3-wire
taco zvc404 control box-switches are set to "norm" + "priority off"
taco low water shutoff
digital honeywell 2-wire t-stats
1 taco circ pump
carlin motor control
ok, so i bleed air from all zones and hot water tank. i then proceeded to bleed fuel line. when i turned power on , it took a minute as usual (i have this s/u at home) and then motor started and ran it's 10 or 15 secs, then shut off. lots of air in line, so i did this 3 times total. 4th time it would not start. on the carlin control i now have a red+ amber light. before it was just amber. now it wont start. few minutes later the lights on the zvc404 go dead....great!, ok, so we check zv wires for continuity-ok there. check t-stat wires for same-ok there. check and confirm 115 volts present at transformer-ok there. fuse ok....check for 24vac on other side of transformer and no good? so it blew for some reason. so i go to supply house and bought a new zvc404. apples and apples. install it, and power it up. all the lights come on. after a minute zv lights come on and zv open up, but still no go on the carlin motor control. still have red and amber light. am i just in "lockout" mode or maybe something else. i'm bothered that transformer blew but fuse didn't. wondering what caused overload. what should i do next? sorry for the long post.
0 · ·