To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Solar Thermal in Thermosiphon- Load Side HX
I've been using the Simple Drainback solar thermal system plumbed in thermosiphon with standard backup systems with excellent success. Attached are images, below is a brief description.
The goal of this method of plumbing is to produce maximum solar fraction with minimal cost associated with addition of solar. Whether using this for DHW, or for radiant, or with solar alone or solar with wood stove auxiliary, this system works, and works well.
The Simple Drainback system is a load side heat exchange system. That means that water in the tank is collector fluid, and potable water is inside the 100' spiral heat exchange coil. The tank has an air space at the top for expansion and drainback function. The load side exchanger is, by design, a very high temperature tank.
By placing the backup tank cleanout slightly above the inlet of the heat exchange coil, colder water at the bottom of the backup tank slips down into the HX, where it's heated and moved back up to the regular tank.
Placing a "T" in that short line provides cold water feed. A check-valve stops backflow. That's it.
Thermosiphon works well with wood stove auxiliary heat as well. Here, the trick is to keep lines short, with ease of fluid movement. Try www.hilkoil for a good stainless heat exchanger in the wood stove.