To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Jumper wire in Vent Damper receptacle on Laars mini-therm JVT75N boiler
Hi, I was wondering if someone could help me please.
I have a Teledyne Laars mini-therm JVT75N boiler and the jumper wire in the power venter/Vent Damper receptacle got accidentally pulled out. I put it back according to diagram A in the installation document C1056A however I have now realized that my receptacle is actually turned 180 degrees from the picture. This means that I actually put the jumper wire between the Y and O wires in the receptacle! See Figure 9c on page 12 of this document for wiring diagram
When I turned the boiler back on and the thermostat turned on there was loud clicking noises every 0.5 seconds. I quickly turned the boiler off and eventually found a wiring diagram that showed my mistake i.e I had put the jumper wire in wrong. I have now managed to put the jumper wire where it should be but now when the thermostat turns on I can see the zone valve open very slowly but the boiler does not come on.
Is it possible for you to predict from the wiring diagram what I might have damaged by putting the jumper wire wrong? Have I damaged the zone valves or the zone pump relay?
I think the loud clicking noise is the same as when the thermostat usually turns on but I am not sure if that noise normally comes from the zone valve itself or the zone pump relay?
Many thanks for any help you can provide.
0 · ·