To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Connecting coal boiler and oil burner
Keystoker Ka 6 coal boiler in series to oil boiler. one thermostat is on Triple Aquastat on oil boiler for zone 1. The other thermostat is connect to a switch for zone 2 that runs it's own circulator. Keystoker Triple Aquastat is running circulator for loop. In doing this Ka is only running on the low side. Oil boiler is powered but low and high is set at 0. How can I wire thermostat to ka so it knows that there is a call for heat in one of the zones. In doing this Ka will run on high & low and will start stoking sooner. Will a R8222D 1014 relay work? If so diagram on wiring.
0 · ·