To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
thankyou fan in a can.....
sprayfoamed insulated house as tight as tight can be,home owner disconnected carbon monoxide alarm as it annoyed him when it went off.sealed boiler room,200,000 btu boiler .fresh air was via a 10"x3" duct.i put a pieceof paper on boiler and it got blown back from chimney backdraft.our temporary solution was a 6" line from outside house into boiler room hooked up to fiel control cas-4 fan in a can.my first time using it and am very impressed.
0 · ·