To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Grumman sunstream control unit
Have an old Grumman Sunstream control unit, previous owner said the heat exchanger was calcified. The solar fluid loop seems very restricted, a garden hose (about 30 - 40 PSI) attached at one end yields a pencil thick stream at the other, about a gallon per minute. Is this normal? The Grundfos UP15 - 42F spins nicely, and the impeller looks good, but i can't get it to pump. There was some black glunk in it and old yellowish antifreeze.
What should the flow be like, and what can i use to remove the calcification from the domestic hot water loop? I already ran CLR thru that loop for several hours (that pump worked fine). Should the CLR have been sufficient, or should i try a muriatic acid solution for good measure? Or white vinegar?
Should i do anything to the 332A panels which are copper?
Thanx for any advice!
0 · ·