To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Leaking HX on Vitodens 200
This HX from a Vitodens 200 was installed 7 or 8 years ago (by others) and poorly maintained. When we were called in to service it, it was loaded with debris and faulting the computer. The vent collar connection for the co-pipe was melted through the inner liner at the top of the boiler. After cleaning the appliance, we found the HX had a leak within the helical SS coil. The replacement HX took 7 days to get to Seattle, but that's another story. Never seen a leaking HX on a Vitodens before.
0 · ·