To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
i got a goodman aepf42 16seer air handler one year old that customer stepped on condensate drain and stressed pan connection which made a big crack. my question is on a horizontal set up and i need to change out horizontal pan can i swing out evaporator coil with piping still connected and not have to pump down and cut open system?i was thinking of loosening clamps and trying this first. goodman says i have to pull coil to get pan out as it sits in pan. i have done other styles by just wiggling the pan from under the coil and sliding it back under. so i am wondering if anyone has done this particular goodman before... thx