To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Cast Iron Baseboard for One-Pipe Steam
Is there such a thing? I've been shopping around, and the only cast iron baseboard I've found is the Burnham Base-Ray (and the Governale Gov-Board, which seems to be nothing more than a rebranded Base-Ray), which comes with 3/4" tappings and is not recommended for one-pipe steam systems.
I want to replace an 8 ft. double fin-tube unit that's way oversized for the room it's in and the supply pipe it's on (1" copper!) with something more appropriately sized, and I'd prefer something that doesn't cool down the minute the steam shuts off. The catch is that it's in front of a big bay window, and there is only 14" between the floor and window.
1983(?) Peerless G-561-W-S
3" drop header, CG400-1090, VXT-24