To get email notification when someone adds to a thread you're following, click on the star in the thread's header and it will turn yellow; click again to turn it off. To edit your profile, click on the gear.
The Wall has a powerful search engine that will go all the way back to 2002. Use "quotation marks" around multiple-word searches. RIGHT-CLICK on the results and choose Open Link In New Window so you'll be able to get back to your results. Happy searching!
In fairness to all, we don't discuss pricing on the Wall. Thanks for your cooperation.
Copper to steel/iron in a closed loop system
What is everyone's opinion on connecting copper to iron/steel in a closed loop hydronic heating system. Boiler to piping, air scoop to piping, iron flow checks, the list goes on and on. I've heard to use anything from a brass valve in between to dielectric unions to just thread 'em together and forget about it.
Has anyone seen leaks from galvanic corrosion due to the connection of these different metals or is it ok?
Thanks for everyone's experience!!!!
Always keep learning: observing what works, and what doesn't. Keep company who are smarter than you.